The incineration will also be equipped with special loading apparatus and mechanisms that enable safe incineration of
solid waste concurrently with liquid sludge. Loading of solid waste may be accomplished via bags. Bidder shall
suggest connection points for sludge, DO and Hot water. Pipings up to those connection points will be on the cost of
that the CEB. All equipment, like pumps, blower fans, compressors and etc forming part of the incineration lot will take
their electrical supply from an electrical panel. The panel should be equipped with proper circuit breakers
and contactors for each component and will allow independent padlocking of their equipment by operators without
intervening from interior the panel. All padlocking works will be reached from outside the electrical panel. The
Electric panel will take supply from an external 3 phase supply.
– the primary compartment shall be fed from an existing switchboard
The panel will be of factory constructed, metal clad and draw-out type in design for outside application.
2.4 Electrical Panel
The panel nominal voltage shall be 415 Vac and its rated insulation voltage shall be 1000 Vac.
– The main compartment shall be fed from an existing switchboard
The panel shall be of factory assembled, metal clad and draw-out type in design for outdoor application.